Temperature & Humidity Sensor
Designed for monitoring humidity levels inside data centers, server rooms, cabinets and other critical facilties.
- measures relative humidity between 10% and 90%.
- with a ±2% accuracy.
- humidity probe made in Switzerland.
- plugs into the base unit.
- powered by the base unit.
- 0U Rack or wall mountable sensor.
- alerts via SNMP Traps, email, SMS or voice calls.
- optional calibration certificates available.
Power Over Ethernet (PoE) - Web. - Modbus. - SNMP. - SNMP Traps. - Email. - SMS. - Voice Call. - Rack Mountable. - Industrial Grade. - Optional Calibration Certificates Some of ServersCheck's customers:
The temperature & humidity sensor
Swiss Made Sensor.
The humidity component inside the ServersCheck sensor is made in Switzerland. It is factory calibrated against several national standards. Final assembly and testing is done in Thailand unless the TAA version is chosen.
Sensor Drifting & Calibration.
How It works.
The ENV-THUM sensor connects to the the base unit. This makes the device an ethernet sensor. The sensor measures the relative humidity and temperature. This sensor is designed to monitor conditions in server rooms and other sensitive area's. Humidity reading is done through the external probe. Alerting via email, SMS, voice call. Integrates with BMS platforms using the Modbus TCP protocol. Or with NMS systems through SNMP GET and SNMP TRAPS.
|Technical Specifications. - Temperature & Humidity Probe (ENV-THUM)|
|.||Temperature Resolution: 0.1°C (0.18)°F precision.|
|Temperature Accuracy: +/- 0.5ºC (+/- 0.9 ºF) over 0ºC to +60ºC.|
|Readings in Celsius or Fahrenheit.|
|Relative Humidity Measurement Range: 0 to 100 % RH.|
|Relative Humidity Resolution or precision: 0.1 % RH and 1 % RH.|
|Relative Humidity Accuracy: +/- 2 % RH between 10 % RH to 90 % RH and +/- 4 % RH below 10 % RH and above 90 % RH.|
|Relative Humidity Long Term Stability: < 1 % RH/year.|
|Operating temperature range: 0ºC to +75ºC (32ºF to +167ºF) in PoE mode.|
|Operating humidity range: < 90% rH (non-condensating).|
|Dimensions: 74 mm (2.9") x 66 mm (2.59") x 22 mm (0.8").|
|Housing: Orange metal case with status led.|
|Sensor connects to & is managed by the SensorGateway. Requires the latest generation of SensorGateway (v5.1)|
|Network communication protocols: SNMPv2,v3 XML HTTP and Modbus TCP|
|Connects via regular straight RJ45 cable to the SensorGateway.
Maxmimum distance between probe and SensorGateway is 10m/33ft
Tips For Avoiding Humidity-Related Server Damage.Most servers will support non-operating humidity in the range of 90%. Actual operating tolerances are quite a bit lower. While moisture in the air isn't necessarily a problem. "Condensing humidity" is water vapor that turns to actual water droplets. It can short out a server as quickly as if you had squirted it with a water hose.
Too low relative humidity levels allow for the build up of static electricity. This static electricity can result in permanent equipment damage. Simply by just touching the IT equipment and causing an ESD discharge.
Humidity conditions are directly related to the temperature in the server room. Water vapor begins to condense once the ambient temperature reaches the "dew point." Because temperatures can vary widely during the day and night, your computer room's dew point changes regularly. It means that you can go from normal operations to "meltdown" in a matter of minutes.
It's important implement a 24/7 monitoring system for relative humidity.
One should be aware that any humidity probe loses its accuracy over time while maintaining precision. This is due to the fact that such sensors breathe air. They come in contact with contaminants and pollutants that will affect the sensors' accuracy. You need to calibrate your sensor at least once per year when used indoor. ServersCheck's lab can provide you with the certification in order to ensure that you have a calibrated humidity sensor that complies to NIST traceability requirements.
Selecting a humidity sensor.There are different humidity sensors on the market. Understanding the differences is important when chosing the right sensor for your application. Selection criteria are:
Precision is fundamentally different from accuracy. "The precision of a measurement system, related to reproducibility and repeatability, is the degree to which repeated measurements under unchanged conditions show the same results." Very few vendors will give you any information regarding precision although this is very important. Testing precision requires scientific instrumentation. At ServersCheck we created a lab with certified climate chambers that reproduce specific conditions. By maintaining such conditions we are able to test the precision of a sensor and issue a certificate for it. Almost no other vendor has that capability. At best they refer you to a 3rd party lab.
Precision is the repeatability, or reproducibility of the measurement. It is not because you have a precise equipment that it is accuracte. Accuracy is the proximity of measurement results to the true value. In the image you can see that the readings have a good accuracy but they fail on precision. They are off compared to the trueness or true value. What is the true value?
The true value is maintained by international standards organizations. In the US, they are maintained by the National Institute of Standards and Technology or more commonly known as the NIST. The Thermodynamic Metrology Group is responsible for the US national standards in respect to humidity. We verify sensors in our lab to the set standards by following an unbroken chain of documentation and incorporating the uncertainties. By using ISO certified and NIST traceable instrumentation we ensure that our tests are not only performed for precision but also for accuracy. How close are the sensor readings to the true value considering factored uncertainty. This is what ServersCheck can provide you though our lab.
Resolution is the smallest change in a measured value it can detect. Resolution is not precision nor is it accuracy. It is the granularity at which changing readings can be detected. Another name for sensor resolution is its sensivity. Our temperature and humidity sensors have a sensitivity of 0.1% relative humidity. This means that if the observed humidity changes for more than 0.1% then it will be detected and returned.
Unlike ServersCheck's sensors, most digital relative humidity sensors are not calibratable. When they lose accuracy, then you will be forced to purchase a new sensor without even knowing if that sensor is accurate. If accurate humidity measurement is key to your project, then make sure you got a calibrated sensor (with certificate). To keep your investment low opt for a vendor, like ServersCheck, that is able to calibrate its sensors so that you don't have to purchase new ones. At ServersCheck we also have a trade-in program: every year we ship you a newly calibrated sensor so that you are always accurate and precise.